Why the temperature drops not be as fast as before? Some end users who use Water Chiller may have such experience, no matter what the chiller is. After using chiller for some period, they would feel that the cooling performance is worse than before. And that`s why chiller maintenance should be done regularly.
The Industrial Water Chiller is a device that provides constant temperature, constant current. They are widely used in the pharmaceutical industry, food industry, plastics industry, machinery industry and other fields. For this question, persons familiar with water chillers stated that generally speaking industrial chillers have a certain life expectancy. The good quality chiller can be used for more than ten years if used carefully and maintained regularly.
[If the chiller was overloaded for a long period of time, the components of the industrial glycol chiller may be affected, which would lead to various failures in the industrial chiller," said a cooling specialist.
There are many reasons for the poor cooling effect of industrial chillers, and the common reason is that industrial chillers were not maintained regularly. [If they were not regularly maintained, it will easily lead to more dust in internal parts of the industrial chiller, and the heat can not be effectively taken away. Also the equipment is in a high load running state for a long time, so the cooling effect is not as good as before."
Normally, as long as the cooling capacity is matched with the heating equipment, except for the failure of the industrial scroll and Screw Water Chiller, the reason for the poor cooling effect of the industrial chiller is that the chiller was not maintained regularly.
Therefore the maintenance of the chiller affects the cooling effect of the equipment. According to reports, in the process of using industrial chillers, users should dismantle and clean the dust-proof net of the chiller regularly, clean the dust on the condenser of the chiller, and periodically replace the circulating cooling water (pure water or distilled water) if there is an auxiliary industrial chiller. Filters require periodic replacement of filter elements to ensure clean water. In addition, the operating temperature of the industrial chiller cannot be too high. If the ambient temperature of the industrial chiller is relatively poor, the cooling effect of the chiller will also be affected.
Some customers have also raised questions about what to do if they encounter a situation where the industrial chiller has a poor cooling effect due to the cause of the malfunction.
The chiller that causes the cooling effect of the chiller to deteriorate is generally in two situations and can respond according to the corresponding problem. First, there is a problem with industrial chiller thermostats that cannot achieve temperature control. It is recommended to contact the after sales technicians to replace the thermostat. Second, the cooling system leaks refrigerant. It is advisable to contact the after sales technician to find the missing point. And refill the refrigerant.
Except for regular maintenance, use the equipment rationally. The author believes that when companies use industrial Glycol Water Chiller, the correct operation method is also very important. Only the correct operation method can guarantee the normal and stable operation of industrial chillers. If there are too many erroneous operation behaviors, it will directly affect the normal use of the equipment. In severe cases, even more failures will occur, affecting the cooling performance of industrial chillers.
Therefore, when companies are using industrial chillers, they need to learn the correct operating methods, regular maintenance, in order to ensure the correct operation of the equipment, and extend the life of the equipment.